Since last week Friday we are seeing some errors on xe-2/0/43 - lvs2009:enp175s0f1d1. We need to re-seat the transceiver to see if this fix the issue if not replace it.
I think all good now on the interface . closing this task. Just replaced the transceiver on the switch side.
Laser bias current : 40.478 mA Laser output power : 0.6830 mW / -1.66 dBm Module temperature : 38 degrees C / 100 degrees F Module voltage : 3.2680 V Receiver signal average optical power : 0.7036 mW / -1.53 dBm