@Marostegui These are ready for you
db1018 and db1022 are confirmed in racktables but are both decommissioned and removed from the rack.
Tue, Nov 14
Wiped, racktables updated
Wiped, racktables updated
wiped, racktables updted
wiped, racktables updated
wiped, racktables updated.
Wiped, removed from racktables
Wed, Nov 8
@Marostegui during my decom checks I found db1015 in this file. Should a replacement be identified?
Looks like the rebuild is complete and all disks are back online
All on-site work is complete assigning to @RobH
Disk has been swapped
Tue, Nov 7
Mon, Nov 6
I have connected the Ripe atlas anchor to iron if you want to load the image.
Fri, Nov 3
@chasemp please try again, I replaced the broken CPU.
Thu, Nov 2
The CPU was replaced and idrac log cleared.
the 2nd interfaces are connected, updated the switch descriptions, I did not enable the ports.
Tested a standard ethernet cable and it works fine. It appears that the custom pinout for the cable is no longer required and each of the cables will need to be re-done.
Mon, Oct 30
Server has been wiped and removed from rack...racktables updated
this has been completed.
I've replaced the console, set it up so it's accessible. Setup all the ports but I am not able to access ports via pmshell. @RobH could you look into this and see if I missed something please.
this server is out of warranty by 6 months. Assigning to @RobH to determine if we should order a new one...probably two.
this server is out of warranty by 6 months. Assigning to @RobH to determine if we should order a new one?
Replaced the disk but this server should be replaced and decommissioned sooner rather than later.
Sat, Oct 28
I am not sure what else can be done here. I’ve replaced the PSUs twice,
upgraded f/w and they continue to burn through the fans. This group of
servers is almost a year out of warranty.
Fri, Oct 27
@Ottomata okay please update task when it's okay to wipe. Thanks
Wed, Oct 25
Dell declined to send the new DIMM, stated that my supporting documentation was insufficient. I swapped the DIMM at A4 to B4 and will need to wait for that to fail before submitting again.
Dell declined the new system board. We are getting another CPU to since that is the part that seems to be broken.
Mon, Oct 23
The controller has been replaced and the server has been powered on. @Marostegui please resolve task when you're comfortable with the new controller.
@chasemp, no unfortunately it does not work that way. I new CPU and motherboard has been requested through Dell. I believe that will fix the issue. The CPU they sent the first time is refurbished so its possible it may have been bad.
@Marostegui the HP tech will be at the data center today to swap the controller. Is the server depooled?
Fri, Oct 20
replaced both psu's in analtyics1037, the psu in an1036 cleared the error and is functioning normally as far as I can tell.
@andrew..wrote that in the wrong ticket
Still no sign of failure from the h/w log....it took awhile last time
Thu, Oct 19
They all have the same problem. I swapped PSU's for both an1036 and 1037 yesterday but still show the failure. The new psu's are failing after a new one is installed. These servers are now out of warranty.
Oct 18 2017
This server's warranty expired 2 years ago. The R720XD's have a history of killing power supplies. I inserted a new power supply and immediately it was fried. This server should be decommissioned sooner rather than later. @Ottomata
Verified that the settings are all correct, the server both racadm and web UI do not show any problems with the power supplies
This server is alread scheduled for decommission. T164341
This PSU on the surface appears to be fine, no LED's and racadm showed it normal. The mgmt U?I showed PS1 failed. Replaced from a recent decom. (out of warranty)