Tue, Apr 13
Mon, Apr 12
Wed, Apr 7
Wed, Mar 24
applied new hostname label
name rack_name position Port Cable ID
cloudvirt1040 D5 22 22,34 5358 ,5359
cloudvirt1041 D5 23 24,32 5360 ,5361
cloudvirt1042 D5 24 25,33 5362 ,5363
cloudvirt1043 D5 25 26,30 5364 ,5365
cloudvirt1044 D5 26 27,31 5366 ,5367
cloudvirt1045 D5 27 28,29 5368 ,5369
cloudvirt1046 D5 28 4,46 5370 ,5371
cloudcephosd1016. rack A4. U40 port 11,13 ID5344,5345
cloudcephosd1017. rack A4. U41. port 22,23 ID5346,5347
cloudcephosd1018. rack A4. U42. port 17,29 ID5348,5349
cloudcephosd1019. rack D4. U31. port 14,15 ID5350,5351
cloudcephosd1020. rack D4. U32. port 8,9 ID53525353
Tue, Mar 23
bast1003 Rack D1 U41 Port24 ID3161
moss-fe1001 A2. U42. Port33 ID5341
moss-fe1002. D4. U41 Port41 ID5342
Wed, Mar 17
Mar 15 2021
Handing over to Chris to finish the 2 we have received
db1176 A1 u6 p14 id1751
db1177 A3 u38 p29 id 1931
db1178 B1 u25 p16 id4020
db1179 B5 u35 p38 id3356
db1180 C3 u20 p6 id2956
db1181 C5 u16 p17 id1846
db1182 D1 u38 p22 id3479
db1183 D3 u38 p44 id3945
db1184 D6 u35 p33 id3946
Mar 9 2021
backup1003 Rack b2 U39 port33 Cableid #5031
cloudgw1001 c8 u29 ports13/19 cableid #5322
cloudgw1002. d5 u21 ports 23/35 cableid #5320.
Mar 7 2021
@RobH if you can clarify racking instructions. I have reviewed racking instructions and what these are replacing mw[1261-1290,1293-1306 Are only in row A&B
Mar 4 2021
@jijiki I stopped by cage briefly this morning and looked at server. I could not get it to boot could be a bad cpu or main board.
Mar 1 2021
@fgiunchedi Sorry for delays i had ran into where i was missing the right torques tool to remove pci riser card. after i removed riser card i found the 10g ports are part of the main board. I am unable to swap over. unlike dell we usually have an additional card for 10g. I apologize for the back and forth on this ticket
Replaced Failed Hard drive.
Feb 25 2021
Thanks. I was mistaken that network dns was done by fundraising
Feb 24 2021
Racked and cabled 1 host
Racked & cabled host handing over to Chris for configuration
Ms-backup1001 A4 u4 p3 id5322.
Ms-backup1001. C2 U41 P41 ID5587
Decommissioned server updated netbox added to decommissioned area
replaced DIMM A8 if error returns recommend running
Feb 22 2021
@RobH replaced cable. link light on aqs1014
Created dell Service ticket
Confirmed: Service Request 1052329386 was successfully submitted.
@fgiunchedi ms-be1017 has been swapped into place of ms-be1034. Will we be resurrecting the name ms-be1017 or renaming to ms-be1034? This will most likely need a re imaged.
Feb 19 2021
an-worker1129 verified host cable is moved to port 12
an-worker1139 corrected dac cable for host moved to port 25
memory swap completed @Marostegui
Feb 18 2021
Unable to update using DVD Iso is 10gb. Dual layer dvd is only 8.5gb. I was able to update firmware using ilo and virtual drive. previous veresion 2.50 Sep 23 2016, current version 2.74 May 08 2020
@jcrespo Is host still down can maintenance be preformed on host?
racked & cabled, bios configured, network configured. handing over to Rob for imaging
Feb 16 2021
@fgiunchedi would you be ok with chassis swap using ms-be1018 recently decommissioned?
@RobH Checked all three host no issue with DAC possibly port is turned off for two host
https://netbox.wikimedia.org/dcim/devices/3023/ moved dac cable from port 39 to 41. lit up for connection.
https://netbox.wikimedia.org/dcim/devices/3024/ moved from port 21 to 23. has connection now..
https://netbox.wikimedia.org/dcim/devices/3025/ no issues i see with connection with dac
Feb 15 2021
Feb 12 2021
@fgiunchedi replaced failed SFP on switch
@fgiunchedi Was able to get server to boot with minimal configurations 1cpu 1 dimm.
Feb 11 2021
Forgot Monday is holiday Tuesday 11 AM PST?
@EBernhardson would you be available monday to swap Ram being that it is over 90 days since error we can change memory
was able to download HP Service Pack for ProLiant with help with papaul. will be available next week to preform firmware update
Feb 4 2021
dmidecode -t 20 ``` would be very useful to trace physical address of memory we are unsure why it will not return any information. Would you be able to assist?
Feb 3 2021
service pack tool is only available for in warranty devices. Have reached out to Chris /papaul for guidance on getting service Pack tool for out of warranty device. Will follow up this week with HPE waiting for Support Account Reference.
@Cmjohnson netbox is updated racked in C6 U40. port 39
Feb 2 2021
unplug both of the zayo links from the DMARC panel in the cage
PP:0000:103234 ports 3/4
PP:0000:103234 ports 5/6
Jan 28 2021
@EBernhardson we do not have utilities installed like dmidecode or edac-util. having a list of physical addresses of dimms installed might help narrow down which one has a error. we have 3 address for errors most likely same dimm.
Jan 25 2021
replaced Dac cable for an-worker1119 and an-worker1131 @elukey confirmed both are seeing network
Jan 21 2021
@Cmjohnson all host racked and cabled netbox updated
Jan 20 2021
@Cmjohnson. host are racked and cabled netbox is updated
host , port
Jan 19 2021
Jan 14 2021
Jan 11 2021
@LSobanski I will be working on these this week. As long as nothing comes up urgent it should not be that long