Thu, Mar 22
@fgiunchedi All yours.
Wed, Mar 21
mw2267 is fix now
Tue, Mar 20
Mon, Mar 19
Thu, Mar 15
@MoritzMuehlenhoff the cable is connected, please check switch side if the port is active. I have no light on that port.
Wed, Mar 14
- main board replacement
- ILO configuration
- new nic 1 MAC address e0:07:1b:f7:63:68
Tue, Mar 13
Dear Mr Papaul Tshibamba,
Server would not power on
The server was shipped with no screws attached to the IDRAC card on the main board. I attached the IDRAC card with some screws now.
Mon, Mar 12
Yes that is correct we have only 3 shelves 36 disks visible the reason being that we have 3 shelves (36 disks) connected to port 2 and 4 shelves (48 disks) connected to port 1 (port1 is not plugged in for now only port 2) according to the racking schema provided by Rob. See image below for the racking . (multi-chain configuration)
Thu, Mar 8
@MoritzMuehlenhoff will do
@Joe this needs to be assigned first to someone with root access to do the first 2 steps when complete, assign to me.
Wed, Mar 7
Tue, Mar 6
- On the device labeled asw-0603-eqsin, Juniper EX4600, rack 603, please replace the SFP-T (copper SFPs) present in ports 12, 14 and 23 with the QFX-SFP-1GE-T transceivers. And get rid of the old SFP-Ts.
All the servers were racked and wired before leaving Dallas. Will have to unrack them and re-wiring them.
All the normal troubleshooting was done on the server.
- Unplugging the power
- Removing the PSU's for 15 minutes while working on the router
Server will not power on.
- On the device labeled cr1-eqsin, Juniper MX104, top of rack 603, please replace the 4 optics present in the embedded ports (aka not in modules) labeled xe-2/0/0 to xe-2/0/3 with the SFPP-10GE-LR optics. ( This is done )
This server is dead we need to open a case with Dell for main board replacement. When pushing the power button nothing happen on the server.
The DAC needed to be seated on the switch side
@BBlack please check and see if you can get not to the server
Sat, Mar 3
Wed, Feb 28
Power supply was not seal. Fixed
I am good with that. If you want to try another disk.
on each decommissioned servers when the disk is blinking before decommissioning, the disk it label bad so I do not have to use it.
Disks from the decommissioned servers
@Gehel this is all yours
Tue, Feb 27
Mon, Feb 26
Disk placement complete.
- Power drain server
- Reset ILO
Server is back up.
Switch replacement complete.
- Racktables update
- Test serial console of all 3 servers connected to msw-d4-codfw
@Marostegui can you please depool the system for me?
Fri, Feb 23
@RobH Can you please do the switch part and assign back to me ?
Thu, Feb 22
1- Power drain
2- Update all firmware on the system.
Disk replacement complete.
No blinking disk on db2037 all looks good. And ILO is working on my end
@Marostegui Disk in slot 5 is blinking.
Feb 21 2018
Yes we can resolve this
@Marostegui it is all yours. Installation complete .
Feb 20 2018
@RobH Can you please review rack plan for the new wdqs systems and confirm if is is okay and assigned back to me.
asw-b5-codfw ge-5/0/11 cable ID:6103
@chasemp Unfortunately I am afraid this can not be done on labtestneutron2001 because it has only 2 NIS's (eth0 and eth1) .
Do you want me to connect only labtestneutron2002?
Feb 19 2018
stat2001 port information
@chasemp I have no hosts whit the name labneutron2001 and labneutron2002. Are you referring to labtestneutron2001 and labtestneutron2002?
@Marostegui disk replacement complete