Dell will be shipping 1 New CPU by Monday.
Thu, Dec 13
This can be resolved then since i am done with it .
papaul@asw-a-codfw# run show interfaces ge-5/0/8 descriptions Interface Admin Link Description ge-5/0/8 down down DISABLED
This is complete
Wed, Dec 12
same error again at 22:47
Tue, Dec 11
@Marostegui any reason why production DNS is still showing for pc2004?
papaul@asw-b-codfw> show interfaces ge-5/0/35 descriptions Interface Admin Link Description ge-5/0/35 down down DISABLED
For the connection fpc2-fpc8 on fpc2 I will be using xe-2/0/41 and xe-2/0/42
Fresh OS installed on the system. Leaving the system up again to see.
Stress test on the system cam out with no errors.
Mon, Dec 10
The switch is connected to port 48 on scs-a1-codfw
Running Stress test on the system
This looks good now
Sat, Dec 8
Fri, Dec 7
papaul@asw2-a-eqiad# run show interfaces ge-1/0/2 descriptions Interface Admin Link Description ge-1/0/2 up down cam1-a-b-eqiad.eqiad.wmnet
@fgiunchedi all yours
@MoritzMuehlenhoff no there is no server for now which is still in pristine condition right after the OS install. But I am about to install logstatsh200[1-3] once done, I will ping you.
@fgiunchedi the installation is complaining about not finding any swap partition.
Thu, Dec 6
9:40 AM (21 minutes ago)
to me, faidon
Wed, Dec 5
@fgiunchedi please see below.
@RobH any reason why we have to add the servers that we are returning to the decommission tracking Google sheet since that sheet is to keep track of servers and other devices that are decommissioned and have on site.
After 16 hours of hardware diagnostics, the server came up with no error. I have a Call schedule with Dell in 2 hours to discuss about the next step to take.
@Gehel all yours
Tue, Dec 4
@fgiunchedi Please provide partman recipe to use. I have 4x4TB disks
Mon, Dec 3
@fgiunchedi All looks good on the system. You can resolve the task when finished double checking.
update from Dell
@Gehel all first 8 servers are all yours
@Gehel The first 8 servers (elastic2037-elastic2044) are ready. The only thing left is the first puppet run. When running puppet agent on those nodes I am getting the error below. I think you can fix that for me. Thank you.
Replaced all the parts that was shipped to me by Dell (main board, RAID controller, RAID controller interposer board.SAS cable) swapped CPU1 with CPU2 we have the same problem on the server. I email Dell last Friday, waiting for Dell to get back in touch with me.
Fri, Nov 30
@colewhite Thank you I saw that
Thu, Nov 29
Did all the dell engineer recommended above. Waiting to proceed to step 10 .
Please replace the remaining hardware sent.
Wed, Nov 28
@Gehel In this case the racking proposal will not work since those racks are 1G rack. I will update the task description with the new racking proposal.
@Gehel My racking proposal was to rack some of those server in rack 4 of row A,B and D. @ayounsi and I will be working on replacing all the 1G switches in those rack soon with 10G switches; or the new servers came with both 1GB and 10GB NIC's. So my question to you is :
Are you going to use the 10G NIC or 1G NIC?
This is complete at my end. Don't know the service owner so giving it back to you.
Tue, Nov 27
papaul@asw-b-codfw> show interfaces ge-5/0/5 descriptions
Interface Admin Link Description
ge-5/0/5 up up restbase2013
I have replaced the system board on the system. The system is back online. I will be monitoring the system to see if we do have the same problem again. Also I have on site a new : H730P RAID controller card, SAS cable and RAID controller interposer board that Dell shipped to me.
papaul@asw-b-codfw> show interfaces ge-4/0/1 descriptions Interface Admin Link Description ge-4/0/1 up up sessionstore2001